By Tom Coffey, Infrared Training Center
A small cottage (700 sq. ft) outside of Knoxville, TN was completely remodeled from January to March 2010. It was an existing cinder block structure with no insulation except ½ inch of airspace between the nailers and the block wall as well as the empty block core. The R value of existing building walls was approximately 2.97. After the remodel an R-value was calculated and determined to be 12.6.
2 x 4 studs were used to build the interior walls the insulated with 4” of backed fiberglass bat insulation. Old windows were removed and new double pane sash type windows installed during the remodel.
The house was depressurized to approximately 50 Pascal and allowed to equalize for 30 minutes. A thermographic scan was performed after the equalization period. Infiltration was found around the sash windows where the top and bottom pieces join in the corners of the windows.
The installation of the blower door took approximately 30-45 minutes. Reaching the right depressurization took another 30 minutes and the IR scan took another 45 minutes. For a house this size, allowing for the small footprint I did not do an air exchange calculation. The purpose of this exercise was to determine if the house remodel and adding insulation was sufficient to keep the house at a comfortable level during East Tennessee summers and winters. It was determined during the remodel process that R-13 insulation in the walls and R-19 insulation in the ceilings would be sufficient for the weather conditions in this area of the country.